1. Remove three screws (1) and cover (2).
Using multimeter, check for continuity of fluorescent lamps, ballast,
no continuity is present, replace defective fluorescent lamp,
ballast, or wiring.
W A R N I N G
This fixture contains voltage that is dangerous if
Before replacing fixed roof area ceiling
light, set all circuit breakers and switches to OFF
1. Remove three screws (1) and cover (2) from fixed roof area ceiling
light (3) .