Table 4-1. UNIT PREVENTIVE MAINTENANCE CHECKS AND SERVICES (PMCS)
W - Weekly
M - Monthly
Q - Quarterly
ITEM TO BE
Lethal voltage is present when light set is connected to power source. Disconnect from
power source before inspecting or repairing any electrical component. Be careful not to
contact electrical connections. Electrical shock and death may result from failure to heed
Check male (1) and female
cable assemblies for (continued)physical damage to plug
or insulation. If damaged, turn in to higher level maintenance.
Check for security and proper functioning of ON/ OFF switch (3),
fuseholder (4), and lamp (5). If damaged, turn in to higher level
Inspect storage container latches (6), hinges (7), and handles (8) for
security/serviceability. Check for missing padding (9). If damaged, turn
in to higher level maintenance.
If MCPS is in use, refer Assemblies to Table 2-2 for preventive
maintenance procedures. If MCPS is in storage, remove from storage
and set up in accordance with Chapter II of this manual.