electrical system and a remote temperature probe.
may be repaired be wrapping with vinyl tape. Replace
harness assembly if individual wires are cut or other wise
Remove remote temperature
harness assembly (72, fig. 6-22) according to sequence
g. Installation. Install the remote temperature
sensing harness in reverse order of removal using figure
(1) Open circuit breaker panel cover.
(2) Remove circuit breaker panel per
identification, and observing the following.
(3) Remove terminal board cover (65) and
in distribution box and install electrical leads in
remove nut (69), lockwasher (70) and washer (71) from
terminals 1 through 3 on TB6 terminal board (68).
Remove the electrical leads.
and nuts (69) on terminals 1 through 3 of TB6 terminal
(4) Remove nuts (80), washer (81) and
board (68). Replace terminal board cover (65) on TB6
screws (82) to remove J38 connector (84) from the
terminal board (68).
distribution box. Remove connector cover (83) from
(3) Position J38 connector (84) into mounting
hole on distribution box and secure with screws (82),
(5) Remove the remote temperature sensing
washers (81), and nuts (80).
harness (72) from the distribution box.
(4) Place circuit breaker panel in position on
distribution box and secure with screws.
temperature sensing harness to replace damaged parts
Wire and Terminal Assemblies
a. General. The wire and terminal assemblies
d. Assembly. Assemble harness assembly in
provide for interconnection of the power distribution box
electrical system. The wire and terminal assemblies
guide and observing the following.
consist of a single wire with a terminal lug on each end.
(2) Crimp to secure.
b. Removal. Remove loose wires according to
continuity checking device to check continuity of wiring
referring to table 6-2 for terminal identification and
individual wires. Continuity must not exist between
observing the following.
connector pins or between connector pins and connector
(1) Open circuit breaker panel cover door.
shell. Replace harness assembly if continuity test
(2) Remove screw to disconnect electrical
indicates defective wires or connection.
wire X498A12 (88, fig. 6-22) from terminal 2 on CB15
circuit breaker (108). Disconnect other end of wire from
If possible, straighten any bent
terminal 2 S8 toggle switch (85).
connector pins. Inspect wires for abrasion and cuts )f
(3) Disconnect wires X498B12 and X498C12
insulation. Minor cuts and abrasions are acceptable and
(86, 87) from S8, S9, and S10 toggle switches (85).