Section II. CONTROL COMPONENTS
harness and receptacle are installed on shelter serial No.
1 thru 184 only.
Remove the exterior harness and
This section provides instructions for replacement. of
receptacle (4, FO-3).]Remove the interior harness and
those items considered as components of the
conditioned air control system. They consist of a remote
Install the interior and exterior
temperature sensor receptacle and a humidifier
receptacle and harness assemblies as described in
receptacle used only when the shelter is designated. as
paragraphs 6(-15g and 6-28.
a surgical unit.
7-5. Humidifier Receptacle and Harness Assembly
7-4. Remote Temperature Sensor Receptacle and -
a. General. The humidifier receptacle and harness
a. General. The remote temperature sensor harness
assembly (10. fig. 6-7, sheet 1 of 5) provides for
and receptacle provide a mean of interconnecting a
connection of a humidifier to control the humidity inside
temperature sensor from the shelter interior to the
remote conditioned air source for precise temperature
b. Removal. Remove the humidifier receptacle and
control of the shelter air. The harness assembles
consist of an exterior receptacle and harness which runs
c. Installation. Install the humidifier receptacle, and
through the shelter electrical raceway to the distribution
harness assembly as described in paragraph 6-f.
box where it connects to the interior receptacle and
harness assembly. The remote temperature sensor
Change 1 7-3